Welcome to Jiujiang fire fighting equipment Co., Ltd
ADD：No.1,Daqiao Road,Yujiahe,Lianxi District,Jiujiang City,Jiangxi province,China
Jiujiang fire fighting equipment Co., Ltd © CopyRights
Jiujiang fire fighting equipment Co., Ltd
Fire and rescue lighting rope JZ50J-C
Rated voltage: AC220V
The rated voltage: ≥10cd/m2
Tensile resistance: ≥ 300N
The highest surface temperature: ≤60℃
The compressive strength: 1500V±100V
The jz50-c fire rescue lighting line has the characteristics of anti-aging, anti-seismic, safe, energy-saving and
long service life. The control box has the functions of anti-leakage (electric shock), overload (short circuit)
protection and so on. Used for Underground stores, warehouses, caves, tunnels and other dark environment in the
rescue, detection of disaster, rescue escape.
1. Open the power distribution control box and insert the input cable plug into the power distribution box input
socket. Plug the other end of the input cable into the power supply.
2. Insert the lifesaving light line plug into the outlet socket of the distribution box output end.
3. When the connection is completed, close the protection switch, and then close the no. 1 (or no. 2) switch, and
the lighting line will be on.
4. If the working length is not enough, the wire plate can be connected through series interface (as shown in the
figure below) to reach the required working length.
Note: only 4 disks can be connected within 50m. If the connection is excessive, the whole system will be damaged due
to excessive current.
1. When rewinding, turn the beginning to the OFF (OFF) position, disconnect the input cable from the power supply,
remove the plug from the distribution box, and then remove the lifesaving lighting line at the output end.
2. Wipe clean with a clean soft cloth or sponge, and roll it up in a neat and orderly manner. When rolling up, please
note that the direction of the plug of the lifesaving lighting line is the direction of escape, and the front-end
guide film should be green.
3. It is strictly prohibited to strike or clamp with metal tools, because the broken bulb will cause a section of
wire body not to light up. It is strictly prohibited to make severe impact on the distribution box, causing adverse
4, distribution box before the use should check the switch operating performance: when switching power supply, switch
to ON (open) position, press the yellow column experiment, should switch back to OFF (closed) position, blue leakage
When the column pops up, it proves that the distribution box works normally and can be used safely. If the yellow
test column is pressed, the blue indicator column does not pop up, the power switch cannot return to the OFF(OFF)
position, the distribution box is prohibited.
5. When in use, the blue indicator column must be pressed, and the switch must be turned ON (ON) to play the control
function of the power distribution box.
6. The leakage circuit breaker only protects the leakage of electricity when the load touches the charged object and
the ground, and does not protect the electric shock caused by contacting two lines of the circuit at the same time.
7. The leakage circuit breaker shall be inspected before use. Press the "T" button (pressing time shall not exceed
1s) when the power is turned on. If the leakage circuit breaker is abnormal,
8. After opening the box, the user must check whether the product is in good condition, whether the exposed metal is
rusty, and whether the product is defective due to poor transportation and storage. If the above phenomenon occurs,
the product cannot be used
Please contact the manufacturer in time.